AHU-1.CHWV-O
type: Cooling Command
type: Valve Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.CHWV-O

AHU-1.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.DA-T

AHU-1.DAT-WSP
type: Discharge Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.DAT-WSP

AHU-1.DPR.DPR-O
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.DMPR-O

AHU-1.EF-.EF-RESET
type: Fan Reset Command
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.EF-RESET

AHU-1.EF2-.EF2-A
type: Overload Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.EF2-A.Alarm1

AHU-1.EF2-.EF2-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.EF2-C

AHU-1.EF2-.EF2-S
type: Fan Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.EF2-S

AHU-1.EF4-.EF4-A
type: Overload Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.EF4-A.Alarm1

AHU-1.EF4-.EF4-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.EF4-C

AHU-1.EF4-.EF4-S
type: Fan Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.EF4-S

AHU-1.FLTR-S
type: Filter Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.FLTR-S.Alarm1

AHU-1.HWV-O
type: Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.HWV-O

AHU-1.MA-T
type: Mixed Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.MA-T

AHU-1.OA-T
type: Outside Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.OA-T

AHU-1.OCC-C
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.OCC-C

AHU-1.RA-T
type: Return Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.RA-T

AHU-1.RF-.RF-A
type: Overload Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.RF-A.Alarm1

AHU-1.RF-.RF-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.RF-C

AHU-1.RF-.RF-RESET
type: Fan Reset Command
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.RF-RESET

AHU-1.RF-.RF-S
type: Fan Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.RF-S

AHU-1.SF-.SF-A
type: Overload Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.SF-A.Alarm1

AHU-1.SF-.SF-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.SF-C

AHU-1.SF-.SF-RESET
type: Fan Reset Command
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.SF-RESET

AHU-1.SF-.SF-S
type: Fan Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.SF-S

AHU-1.VVTZN-T
type: VVT
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-1.VVTZN-T

AHU-2.BLDG-P
type: Building Air Static Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.BLDG-P

AHU-2.BLDGP-SP
type: Building Air Static Pressure Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.BLDGP-SP

AHU-2.CHWV-O
type: Cooling Command
type: Valve Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.CHWV-O

AHU-2.DA-P
type: Discharge Air Static Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.DA-P

AHU-2.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.DA-T

AHU-2.DAP-SP
type: Discharge Air Static Pressure Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.DAP-SP

AHU-2.DAT-WSP
type: Discharge Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.DAT-WSP

AHU-2.FLTR-S
type: Filter Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.FLTR-S.Alarm1

AHU-2.HWV-O
type: Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.HWV-O

AHU-2.MA-T
type: Mixed Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.MA-T

AHU-2.OA-T
type: Outside Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.OA-T

AHU-2.OAD.OAD-O
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.OAD-O

AHU-2.OCC-C
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.OCC-C

AHU-2.RA-T
type: Return Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.RA-T

AHU-2.RF-.RF-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.RF-C

AHU-2.RF-.RF-O
type: Speed Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.RF-O

AHU-2.RF.RFVFD-A
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.RFVFD-A.Alarm1

AHU-2.SF-.SF-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.SF-C

AHU-2.SF-.SF-O
type: Speed Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.SF-O

AHU-2.SF.SFVFD-A
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.SFVFD-A.Alarm1

AHU-2.VAV-CLG
type: Cooling Demand
type: VAV
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-2.VAV-CLG

AHU-3.DPR.DPR-O
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.DPR-O

AHU-3.ECON.ECONDIF
type: Differential Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.ECONDIF

AHU-3.FLTR-S
type: Filter Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.FLTR-S.Alarm1

AHU-3.MA-T
type: Mixed Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.MA-T

AHU-3.MALL
type: Mixed Air Temperature Low Limit Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.MALL

AHU-3.MAT-SP
type: Mixed Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.MAT-SP

AHU-3.MINPOSSP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.MINPOSSP

AHU-3.OA-T
type: Outside Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.OA-T

AHU-3.OCC-S
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.OCC-S

AHU-3.RA-T
type: Return Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.RA-T

AHU-3.SDWN-C
type: Shutdown Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.SDWN-C

AHU-3.SF-.SF-A
type: Overload Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.SF-A.Alarm1

AHU-3.SF-.SF-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.SF-C

AHU-3.SF-.SF-S
type: Fan Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.SF-S

AHU-3.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.ZN-T

AHU-3.ZNT-SP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.AHU-3.ZNT-SP

CentralPlant.BLR.BLR-A
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.BLR-A.Alarm1

CentralPlant.BLR.BLR-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.BLR-C

CentralPlant.CH-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CH-C

CentralPlant.CH-S
type: On Off Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CH-S

CentralPlant.CHP3-RST
type: Reset Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHP3-RST

CentralPlant.CHP4-RST
type: Reset Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHP4-RST

CentralPlant.CHW-C
type: Chilled Water System Enable Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHW-C

CentralPlant.CHW-SP
type: Chilled Water Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHW-SP

CentralPlant.CHW-VLV
type: Chilled Water Valve
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHW-VLV

CentralPlant.CHWP.CHWP3-A
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWP3-A.Alarm1

CentralPlant.CHWP.CHWP3-C
type: Pump Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWP3-C

CentralPlant.CHWP.CHWP3-S
type: Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWP3-S

CentralPlant.CHWP.CHWP4-A
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWP4-A.Alarm1

CentralPlant.CHWP.CHWP4-C
type: Pump Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWP4-C

CentralPlant.CHWP.CHWP4-S
type: Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWP4-S

CentralPlant.CHWR-T
type: Chilled Water Return Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWR-T

CentralPlant.CHWS-T
type: Chilled Water Supply Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.CHWS-T

CentralPlant.HTW-C
type: Hot Water System Enable Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HTW-C

CentralPlant.HWP.HWP1-A
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP1-A.Alarm1

CentralPlant.HWP.HWP1-C
type: Pump Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP1-C

CentralPlant.HWP.HWP1-RST
type: Reset Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP1-RST

CentralPlant.HWP.HWP1-S
type: Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP1-S

CentralPlant.HWP.HWP2-A
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP2-A.Alarm1

CentralPlant.HWP.HWP2-C
type: Pump Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP2-C

CentralPlant.HWP.HWP2-RST
type: Reset Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP2-RST

CentralPlant.HWP.HWP2-S
type: Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWP2-S

CentralPlant.HWR-T
type: Hot Water Return Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWR-T

CentralPlant.HWS-T
type: Hot Water Supply Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.HWS-T

CentralPlant.OA-T
type: Outside Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.OA-T

CentralPlant.OCC-C
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.OCC-C

CentralPlant.PLANT-LEAD
type: Lead Lag
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.CentralPlant.PLANT-LEAD

Override-Alarm.GEN-ALM
type: Alarm
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.Override-Alarm.GEN-ALM

VAV1-1.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.BOXHTG

VAV1-1.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.BOXMODE

VAV1-1.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.CMAXFLO

VAV1-1.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.COMMONSP

VAV1-1.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.CPIDPV

VAV1-1.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.DA-T

VAV1-1.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.DPR-C

VAV1-1.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.DMPRPOS

VAV1-1.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.OCCHTGFL

VAV1-1.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.S-VP

VAV1-1.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.SUPFLOSP

VAV1-1.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.SUPFLOW

VAV1-1.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.W-C-ADJ

VAV1-1.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-1.ZN-T

VAV1-2.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.BOXHTG

VAV1-2.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.BOXMODE

VAV1-2.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.CMAXFLO

VAV1-2.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.COMMONSP

VAV1-2.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.CPIDPV

VAV1-2.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.DA-T

VAV1-2.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.DPR-C

VAV1-2.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.DMPRPOS

VAV1-2.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.OCCHTGFL

VAV1-2.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.S-VP

VAV1-2.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.SUPFLOSP

VAV1-2.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.SUPFLOW

VAV1-2.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.W-C-ADJ

VAV1-2.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-2.ZN-T

VAV1-3.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.BOXHTG

VAV1-3.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.BOXMODE

VAV1-3.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.CMAXFLO

VAV1-3.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.COMMONSP

VAV1-3.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.CPIDPV

VAV1-3.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.DA-T

VAV1-3.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.DPR-C

VAV1-3.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.DMPRPOS

VAV1-3.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.OCCHTGFL

VAV1-3.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.S-VP

VAV1-3.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.SUPFLOSP

VAV1-3.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.SUPFLOW

VAV1-3.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.W-C-ADJ

VAV1-3.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-3.ZN-T

VAV1-4.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.BOXHTG

VAV1-4.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.BOXMODE

VAV1-4.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.CMAXFLO

VAV1-4.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.COMMONSP

VAV1-4.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.CPIDPV

VAV1-4.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.DA-T

VAV1-4.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.DPR-C

VAV1-4.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.DMPRPOS

VAV1-4.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.OCCHTGFL

VAV1-4.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.S-VP

VAV1-4.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.SUPFLOSP

VAV1-4.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.SUPFLOW

VAV1-4.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.W-C-ADJ

VAV1-4.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-4.ZN-T

VAV1-5.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.BOXHTG

VAV1-5.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.BOXMODE

VAV1-5.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.CMAXFLO

VAV1-5.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.COMMONSP

VAV1-5.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.CPIDPV

VAV1-5.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.DA-T

VAV1-5.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.DPR-C

VAV1-5.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.DMPRPOS

VAV1-5.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.OCCHTGFL

VAV1-5.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.S-VP

VAV1-5.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.SUPFLOSP

VAV1-5.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.SUPFLOW

VAV1-5.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.W-C-ADJ

VAV1-5.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV1-5.ZN-T

VAV2-1.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.BOXHTG

VAV2-1.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.BOXMODE

VAV2-1.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.CMAXFLO

VAV2-1.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.COMMONSP

VAV2-1.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.CPIDPV

VAV2-1.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.DA-T

VAV2-1.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.DPR-C

VAV2-1.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.DMPRPOS

VAV2-1.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.OCCHTGFL

VAV2-1.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.S-VP

VAV2-1.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.SUPFLOSP

VAV2-1.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.SUPFLOW

VAV2-1.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.W-C-ADJ

VAV2-1.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-1.ZN-T

VAV2-10.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.BOXHTG

VAV2-10.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.BOXMODE

VAV2-10.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.CMAXFLO

VAV2-10.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.COMMONSP

VAV2-10.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.CPIDPV

VAV2-10.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.DA-T

VAV2-10.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.DPR-C

VAV2-10.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.DMPRPOS

VAV2-10.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.OCCHTGFL

VAV2-10.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.S-VP

VAV2-10.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.SUPFLOSP

VAV2-10.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.SUPFLOW

VAV2-10.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.W-C-ADJ

VAV2-10.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-10.ZN-T

VAV2-11.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.BOXHTG

VAV2-11.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.BOXMODE

VAV2-11.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.CMAXFLO

VAV2-11.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.COMMONSP

VAV2-11.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.CPIDPV

VAV2-11.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.DA-T

VAV2-11.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.DPR-C

VAV2-11.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.DMPRPOS

VAV2-11.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.OCCHTGFL

VAV2-11.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.S-VP

VAV2-11.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.SUPFLOSP

VAV2-11.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.SUPFLOW

VAV2-11.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.W-C-ADJ

VAV2-11.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-11.ZN-T

VAV2-12.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.BOXHTG

VAV2-12.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.BOXMODE

VAV2-12.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.CMAXFLO

VAV2-12.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.COMMONSP

VAV2-12.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.CPIDPV

VAV2-12.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.DA-T

VAV2-12.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.DPR-C

VAV2-12.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.DMPRPOS

VAV2-12.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.OCCHTGFL

VAV2-12.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.S-VP

VAV2-12.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.SUPFLOSP

VAV2-12.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.SUPFLOW

VAV2-12.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.W-C-ADJ

VAV2-12.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-12.ZN-T

VAV2-2.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.BOXHTG

VAV2-2.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.BOXMODE

VAV2-2.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.CMAXFLO

VAV2-2.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.COMMONSP

VAV2-2.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.CPIDPV

VAV2-2.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.DA-T

VAV2-2.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.DPR-C

VAV2-2.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.DMPRPOS

VAV2-2.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.OCCHTGFL

VAV2-2.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.S-VP

VAV2-2.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.SUPFLOSP

VAV2-2.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.SUPFLOW

VAV2-2.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.W-C-ADJ

VAV2-2.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-2.ZN-T

VAV2-3.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.BOXHTG

VAV2-3.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.BOXMODE

VAV2-3.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.CMAXFLO

VAV2-3.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.COMMONSP

VAV2-3.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.CPIDPV

VAV2-3.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.DA-T

VAV2-3.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.DPR-C

VAV2-3.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.DMPRPOS

VAV2-3.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.OCCHTGFL

VAV2-3.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.S-VP

VAV2-3.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.SUPFLOSP

VAV2-3.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.SUPFLOW

VAV2-3.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.W-C-ADJ

VAV2-3.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-3.ZN-T

VAV2-4.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.BOXHTG

VAV2-4.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.BOXMODE

VAV2-4.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.CMAXFLO

VAV2-4.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.COMMONSP

VAV2-4.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.CPIDPV

VAV2-4.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.DA-T

VAV2-4.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.DPR-C

VAV2-4.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.DMPRPOS

VAV2-4.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.OCCHTGFL

VAV2-4.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.S-VP

VAV2-4.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.SUPFLOSP

VAV2-4.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.SUPFLOW

VAV2-4.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.W-C-ADJ

VAV2-4.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-4.ZN-T

VAV2-5.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.BOXHTG

VAV2-5.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.BOXMODE

VAV2-5.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.CMAXFLO

VAV2-5.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.COMMONSP

VAV2-5.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.CPIDPV

VAV2-5.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.DA-T

VAV2-5.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.DPR-C

VAV2-5.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.DMPRPOS

VAV2-5.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.OCCHTGFL

VAV2-5.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.S-VP

VAV2-5.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.SUPFLOSP

VAV2-5.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.SUPFLOW

VAV2-5.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.W-C-ADJ

VAV2-5.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-5.ZN-T

VAV2-6.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.BOXHTG

VAV2-6.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.BOXMODE

VAV2-6.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.CMAXFLO

VAV2-6.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.COMMONSP

VAV2-6.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.CPIDPV

VAV2-6.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.DA-T

VAV2-6.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.DPR-C

VAV2-6.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.DMPRPOS

VAV2-6.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.OCCHTGFL

VAV2-6.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.S-VP

VAV2-6.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.SUPFLOSP

VAV2-6.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.SUPFLOW

VAV2-6.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.W-C-ADJ

VAV2-6.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-6.ZN-T

VAV2-7.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.BOXHTG

VAV2-7.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.BOXMODE

VAV2-7.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.CMAXFLO

VAV2-7.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.COMMONSP

VAV2-7.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.CPIDPV

VAV2-7.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.DA-T

VAV2-7.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.DPR-C

VAV2-7.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.DMPRPOS

VAV2-7.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.OCCHTGFL

VAV2-7.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.S-VP

VAV2-7.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.SUPFLOSP

VAV2-7.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.SUPFLOW

VAV2-7.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.W-C-ADJ

VAV2-7.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-7.ZN-T

VAV2-8.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.BOXHTG

VAV2-8.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.BOXMODE

VAV2-8.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.CMAXFLO

VAV2-8.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.COMMONSP

VAV2-8.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.CPIDPV

VAV2-8.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.DA-T

VAV2-8.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.DPR-C

VAV2-8.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.DMPRPOS

VAV2-8.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.OCCHTGFL

VAV2-8.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.S-VP

VAV2-8.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.SUPFLOSP

VAV2-8.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.SUPFLOW

VAV2-8.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.W-C-ADJ

VAV2-8.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-8.ZN-T

VAV2-9.BOXHTG
type: Heating Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.BOXHTG

VAV2-9.BOXMODE
type: Box Mode Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.BOXMODE

VAV2-9.CMAXFLO
type: Max Cooling Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.CMAXFLO

VAV2-9.COMMONSP
type: Zone Air Temperature Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.COMMONSP

VAV2-9.CPIDPV
type: Cooling Demand
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.CPIDPV

VAV2-9.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.DA-T

VAV2-9.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.DPR-C

VAV2-9.DPR.DPRPOS
type: Damper Position Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.DMPRPOS

VAV2-9.OCCHTGFL
type: Min Occupied Heating Supply Air Flow Setpoint Limit
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.OCCHTGFL

VAV2-9.S-VP
type: Supply Air Velocity Pressure Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.S-VP

VAV2-9.SUPFLOSP
type: Supply Air Flow Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.SUPFLOSP

VAV2-9.SUPFLOW
type: Supply Air Flow Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.SUPFLOW

VAV2-9.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.W-C-ADJ

VAV2-9.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VAV2-9.ZN-T

VVT-1.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.DA-T

VVT-1.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.DPR-C

VVT-1.MAXDMP
type: Supply Air Damper Max Position Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.MAXDMP

VVT-1.MINDMP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.MINDMP

VVT-1.OCC-SPT
type: Occupied Temperature Setpoint
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.OCC-SPT

VVT-1.OCCCMD
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.OCCCMD

VVT-1.OCCDB
type: Occupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.OCCDB

VVT-1.OCCSTS
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.OCCSTS

VVT-1.UNOCDB
type: Unoccupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.UNOCDB

VVT-1.UNOSETP
type: Unoccupied Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.UNOSETP

VVT-1.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.W-C-ADJ

VVT-1.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.ZN-T

VVT-1.ZONEDMD
type: Zone Demand
pointname: NAE35-OrindaLib/N2 Trunk.VVT-1.ZONEDMD

VVT-2.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.DA-T

VVT-2.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.DPR-C

VVT-2.MAXDMP
type: Supply Air Damper Max Position Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.MAXDMP

VVT-2.MINDMP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.MINDMP

VVT-2.OCC-SPT
type: Occupied Temperature Setpoint
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.OCC-SPT

VVT-2.OCCCMD
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.OCCCMD

VVT-2.OCCDB
type: Occupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.OCCDB

VVT-2.OCCSTS
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.OCCSTS

VVT-2.UNOCDB
type: Unoccupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.UNOCDB

VVT-2.UNOSETP
type: Unoccupied Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.UNOSETP

VVT-2.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.W-C-ADJ

VVT-2.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.ZN-T

VVT-2.ZONEDMD
type: Zone Demand
pointname: NAE35-OrindaLib/N2 Trunk.VVT-2.ZONEDMD

VVT-3.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.DA-T

VVT-3.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.DPR-C

VVT-3.MAXDMP
type: Supply Air Damper Max Position Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.MAXDMP

VVT-3.MINDMP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.MINDMP

VVT-3.OCC-SPT
type: Occupied Temperature Setpoint
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.OCC-SPT

VVT-3.OCCCMD
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.OCCCMD

VVT-3.OCCDB
type: Occupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.OCCDB

VVT-3.OCCSTS
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.OCCSTS

VVT-3.UNOCDB
type: Unoccupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.UNOCDB

VVT-3.UNOSETP
type: Unoccupied Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.UNOSETP

VVT-3.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.W-C-ADJ

VVT-3.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.ZN-T

VVT-3.ZONEDMD
type: Zone Demand
pointname: NAE35-OrindaLib/N2 Trunk.VVT-3.ZONEDMD

VVT-4.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.DA-T

VVT-4.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.DPR-C

VVT-4.MAXDMP
type: Supply Air Damper Max Position Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.MAXDMP

VVT-4.MINDMP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.MINDMP

VVT-4.OCC-SPT
type: Occupied Temperature Setpoint
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.OCC-SPT

VVT-4.OCCCMD
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.OCCCMD

VVT-4.OCCDB
type: Occupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.OCCDB

VVT-4.OCCSTS
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.OCCSTS

VVT-4.UNOCDB
type: Unoccupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.UNOCDB

VVT-4.UNOSETP
type: Unoccupied Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.UNOSETP

VVT-4.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.W-C-ADJ

VVT-4.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.ZN-T

VVT-4.ZONEDMD
type: Zone Demand
pointname: NAE35-OrindaLib/N2 Trunk.VVT-4.ZONEDMD

VVT-5.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.DA-T

VVT-5.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.DPR-C

VVT-5.MAXDMP
type: Supply Air Damper Max Position Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.MAXDMP

VVT-5.MINDMP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.MINDMP

VVT-5.OCC-SPT
type: Occupied Temperature Setpoint
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.OCC-SPT

VVT-5.OCCCMD
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.OCCCMD

VVT-5.OCCDB
type: Occupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.OCCDB

VVT-5.OCCSTS
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.OCCSTS

VVT-5.UNOCDB
type: Unoccupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.UNOCDB

VVT-5.UNOSETP
type: Unoccupied Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.UNOSETP

VVT-5.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.W-C-ADJ

VVT-5.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.ZN-T

VVT-5.ZONEDMD
type: Zone Demand
pointname: NAE35-OrindaLib/N2 Trunk.VVT-5.ZONEDMD

VVT-6.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.DA-T

VVT-6.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.DPR-C

VVT-6.MAXDMP
type: Supply Air Damper Max Position Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.MAXDMP

VVT-6.MINDMP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.MINDMP

VVT-6.OCC-SPT
type: Occupied Temperature Setpoint
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.OCC-SPT

VVT-6.OCCCMD
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.OCCCMD

VVT-6.OCCDB
type: Occupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.OCCDB

VVT-6.OCCSTS
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.OCCSTS

VVT-6.UNOCDB
type: Unoccupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.UNOCDB

VVT-6.UNOSETP
type: Unoccupied Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.UNOSETP

VVT-6.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.W-C-ADJ

VVT-6.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.ZN-T

VVT-6.ZONEDMD
type: Zone Demand
pointname: NAE35-OrindaLib/N2 Trunk.VVT-6.ZONEDMD

VVT-7.DA-T
type: Discharge Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.DA-T

VVT-7.DPR.DPR-C
type: Damper Position Command
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.DPR-C

VVT-7.EF5-.EF5-C
type: On Off Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.EF5-C

VVT-7.MAXDMP
type: Supply Air Damper Max Position Setpoint
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.MAXDMP

VVT-7.MINDMP
type: Supply Air Damper Min Position Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.MINDMP

VVT-7.OCC-SPT
type: Occupied Temperature Setpoint
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.OCC-SPT

VVT-7.OCCCMD
type: Occupancy Command
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.OCCCMD

VVT-7.OCCDB
type: Occupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.OCCDB

VVT-7.OCCSTS
type: Occupied Mode Status
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.OCCSTS

VVT-7.UNOCDB
type: Unoccupied Dead Band
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.UNOCDB

VVT-7.UNOSETP
type: Unoccupied Temperature Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.UNOSETP

VVT-7.W-C-ADJ
type: Thermostat Adjust Setpoint
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.W-C-ADJ

VVT-7.ZN-T
type: Zone Air Temperature Sensor
has site: orinda-public-library
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.ZN-T

VVT-7.ZONEDMD
type: Zone Demand
pointname: NAE35-OrindaLib/N2 Trunk.VVT-7.ZONEDMD

orinda-public-library
type: Site
country: US
num floors: 3
primary function: Library
timezone: America/Los_Angeles